Since 1979, J.E. Johnson, Inc. is your best choice for repair, installation, and service in homes and buildings just like yours in the Great Lakes Bay Region. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that J.E. Johnson, Inc. stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Plumbing, & Furnace Repair in Grand Blanc, MI. Call us today at (800) 646-2690!
A service technician was at the house the same day as the work order was placed.
Response from J.E. Johnson Services, Inc.:
Thank you for taking the time to tell us about your experience. We are thrilled that you had such a great experience with our staff. If you would take a moment to "LIKE" our Facebook page and possibly leave a review there we would greatly appreciate it as we're working to build our social media presence. https://www.facebook.com/jejohnsonheatingcooling/ Julie ~ Business Engagement Coordinator
Matt was wonderful! We have had several service calls from different companies concerning our washing machine. We would think that it was fixed but it would soon break down again. It was very frustrating! Then Matt from J.E. Johnson came to our home and knew exactly what was wrong. He took care of it and now we can do the laundry!! Matt is very knowledgeable and we will definitely call him if another appliance breaks down. He is an asset to this company. Thank you, Matt!!!
Repaired Carrier ac system.
Performed maintenance inspections on heating & cooling systems.
Performed ac maintenance inspection.
Inspection on ac system.
Maintenance inspection on ac system.
Install of Payne 45 mbtuh 80% nat gas upflow furnace
Winter service on Carrier 80% furnace
Performed maintenance inspection on Goodman furnace.
No cool on Goodman condenser.
Customer had no heat. Found ignitor bad. Replaced ignitor. System operating properly.
Furnace leaking water
Furnace leaking water
Bryant furnace with bad inducer assembly. Installed new inducer motor, & furnace is operating properly.